**A. ****Lighting**

a. 15A,120V circuits

1) General: 1200 watts

2) Maximum: 1380 watts

b. 20A,120V circuits

1) General: 1600 watts

2) Maximum: 1900 watts

c. 20A, 277V circuits

1) General: 3000 watts

2) Maximum: 4000 watts

Spare circuits: Approximately 25%

**B. ****Receptacles**

1. Convenience Receptacle- 180 watts per receptacle per NEC

a. 20A,120V circuits per NEC

b. General: 8 outlets

c.Maximum: 10 outlets

2. Appliance Receptacles - check local electrical load for circuit limitations.

Spare circuits: Approximately 25%